ORIGINAL RESEARCH article
Sec. Carbon Capture, Utilization and Storage
Improved Flexibility and Economics of Combined Cycles by Power to Gas
- 1Escuela de Ingeniería y Arquitectura, Universidad de Zaragoza, Zaragoza, Spain
- 2Fundación Agencia Aragonesa Para la Investigación y el Desarrollo (ARAID), Zaragoza, Spain
Massive penetration of renewable energy in the energy systems is required to comply with existing CO2 regulations. Considering current power pools, large shares of renewable energy sources imply strong efficiency and economic penalties in fossil fuel power plants as they are mainly operated to regulate the system and constant shutdowns are expected. Under this framework, the integration of a combined cycle power plant (CCPP) with an energy storage technology such as power to gas (PtG) is proposed to virtually reduce its minimum complaint load through the diversion of instantaneous excess electricity. Power to gas produces hydrogen through water electrolysis, which is later combined with CO2 to produce methane. The main novelty of this study relies in the improved flexibility and economics of combined cycles by means of using power to gas as a tool to reduce the minimum complaint load. The principal objective of the study is the quantification of cost reduction under different scenarios of shutdowns and conventional start-ups. The case study analyses a combined cycle of 400 MWe gross power with a minimum complaint load of 30% that can be virtually reduced to 20% by means of a 40- MWe power-to-gas plant. Eight scenarios are defined to compare the reference case of conventional operation under hot, warm, and cold start-ups with power-to-gas-assisted operation. Additionally, PtG-assisted operation scenarios are analyzed with different loads (30–50–70%). These scenarios also include the consideration of a temporary peak of demand occurring in a period in which dispatch is below the minimum complaint load. Under this situation, the response time of conventional plants is very limited, while PtG-assisted CCPP can rapidly satisfy the peak. The techno-economic model quantifies the required fuel, gross and net power, and emissions as well as total costs and incomes under each scenario and net differential profit in an hourly basis. The analysis of the obtained results does not recommend the operation of the PtG-assisted CCPP at minimum complaint load for hot, warm, or cold start-ups. However, important marginal profits are achieved with the proposed system for part-loads operation over 50% for every sort of start-up, avoiding shutdowns and extending the capacity factor.
Aiming to reduce the greenhouse gas emissions below 40% of the 1990 levels (Paris Agreement of 2015) (United Nations Framework Convention on Climate Change [UNFCCC], 2015), the European Directive 2018/2001 promotes reaching 32% share of renewable energy sources (RES) by 2030 (European Commission, 2018). Moreover, RES share in European electricity production is expected to increase to 53% by 2050 (Capros et al., 2016). However, the transition toward a decarbonized society implies large amounts of variable RES in the energy system, wherein the balance between power generation and demand is difficult (Bailera and Lisbona, 2018; Lisbona et al., 2018). The problem of optimal dispatch and its connection with renewables or natural gas grids is being profusely analyzed in literature (Chen et al., 2018; He et al., 2018, 2020; Wang et al., 2019; Naval et al., 2020).
Traditionally, fossil-based regulation kept the frequency and the voltage of the grid within a stable range. Nowadays, power pools favor RES to the detriment of fossil-based electricity. However, generators and system operators control just 5–10% of the dispatch in RES power plants (the level of control in Spain is about 5%, in Sweden 6%, and in Germany 7%) (Pierre et al., 2011). Therefore, fossil fuel power plants (FFPP) are compelled to perform many start-ups, shutdowns, and load variations to meet demand. These cycling processes deteriorate the equipment, drop the efficiency, worsen specific CO2 emissions, and increase the costs (Gilbert and Sovacool, 2017).
The implications of this issue have been analyzed in literature for energy systems worldwide. In northeastern China, Yin et al. (2017) studied the benefits of curtailing some wind power. They found that the overall income is optimized when the daily average wind curtailment is 2.17%. Despite curtailing some RES, the CO2 emissions do not increase with respect to a scenario in which wind power is completely integrated in the grid. The extra amount of CO2 that would be saved using the surplus wind power is canceled out by the high specific emissions of peak regulation in FFPP.
In Europe, de Groot et al. (2017) analyzed how the share of variable renewable technologies (VRE) influences on the performance of FFPP for different scenarios from 2005 to 2014 (de Groot et al., 2017). When renewable penetration is higher than 15%, they found that the yearly average efficiency of the combined cycle power plant (CCPP) drops by 20 points since full-load operating hours diminishes by 53%. Besides that, Van den Bergh and Delarue (2015) state that the implications of the overall cycling process (i.e., direct start, indirect start, outages, ramping, and efficiency decrease) are overlooked by system operators as they consider only the direct start. If the system operator considered total cycling costs when developing the optimal schedule for 25–40% VRE penetrations, the annual cycling costs of power plants could be reduced at 40%.
In western United States, Lew et al. (2013) studied scenarios with wind and solar penetrations up to 33%. They showed that the increment of emissions associated to cycling processes (+ 0.2% of total CO2 emissions) has a small impact on the CO2 saved because of the curtailment of fossil fuels (-34% of total CO2 emissions). However, the cycling cost may increase to 1.28 US$ per MWh, which is not negligible in the context of reduced generation and revenue.
Actually, incomes from electricity will not cover production costs even if enough flexibility is achieved (Sjoerd Brouwer et al., 2015). Hentschel et al. (2016) showed that the profits barely change with faster ramp rates in combined cycles. Only the reduction of the minimum complaint load (MCL), the minimum load at which the plant can reliably operate before being disconnected out of the grid, may lead to relevant savings, thanks to avoiding the curtailment of incomes (Hentschel et al., 2016; Romeo et al., 2018). Under this framework, the authors propose to use power to gas (PtG) technology to virtually reduce the MCL of a given combined cycle. Instead of shutting down the combined cycle, the electricity production that exceeds demand may be diverted to the PtG energy storage. A similar concept was previously assessed by the authors, in which PtG displaces nuclear power to avoid part-load operation in coal-fired power plants (the average annual efficiency of the FFPP increased from 33.2 to 35.2%) (Bailera et al., 2019c).
Power to gas aggregates different technologies through which electricity is chemically stored in the form of gaseous or liquid chemicals and fuels (Andika et al., 2018; Brynolf et al., 2018; Buttler and Spliethoff, 2018; Allman et al., 2019; Anghilante et al., 2019). Among them, power to methane is one of the most promising long-term storage technologies for the versatility regarding applications and the use of current gas network infrastructures (Götz et al., 2015; Bailera and Lisbona, 2018; Eveloy and Gebreegziabher, 2018; Lewandowska-Bernat and Desideri, 2018; Wulf et al., 2018; Thema et al., 2019). These technologies not only will play an important role in decarbonization of the industry (Baier et al., 2018; Cormos et al., 2018; Di Salvo and Wei, 2019; Chauvy et al., 2020; Rosenfeld et al., 2020), transport (Schemme et al., 2017; Colbertaldo et al., 2019), and building (Bailera et al., 2019b) but also will be needed to balance the power generation with demand under high penetration of variable renewable energies (Bailera and Lisbona, 2018; Eveloy and Gebreegziabher, 2018; Wulf et al., 2018).
In the present work, power to gas uses the part of electricity that the CCPP cannot sell at the moment to produce hydrogen through water electrolysis. Then, this hydrogen is combined with CO2 to produce methane through methanation (Gahleitner, 2013; Giglio et al., 2015; Götz et al., 2015; Jensen et al., 2015; Vandewalle et al., 2015; Bailera et al., 2017a, b; Becker et al., 2019). Several options have been proposed in literature for the supply of CO2. Biogas is an attractive carbon source because it avoids the carbon capture stage and methanation heat could be used in the digestion process (Angelidaki et al., 2018; Anghilante et al., 2019). Nevertheless, the most common and simplest integration that directly uses CO2 from carbon capture in the combined cycle is considered as more realistic for the application investigated. Besides that, in this work, the synthetic natural gas coming from the PtG process is used as fuel for the combined cycle itself to reduce the operating cost.
The novelty of this paper underlies in the improved flexibility and economics of combined cycles by using power to gas as method to reduce the minimum complaint load. The objective is to compare and quantify this proposal with different scenarios of shutdowns and conventional start-ups.
In this study, we assess a combined cycle of 400 MWe gross power. The auxiliaries of the plant consume 2.5% of this power output. The minimum complaint load is 30% (Nalbandian-Sugden, 2016), but it can be virtually reduced to 20% by using PtG. This power-to-gas plant manages up to 40 MWe (i.e., 10% of the gross power of the CCPP). The overall efficiency of the energy storage is assumed constant at 60% (power to methane), accounting for polymer electrolyte membrane electrolysis (75% higher heating value, HHV) (Matute et al., 2019) and methanation (80% HHV) (Bailera et al., 2019a). Figure 1 illustrates the system under study.
Figure 1. Integration of power to gas and combined cycle power plant in the energy system: (A) Dispatch below minimum complaint load (MCL) diverting surplus electricity to power to gas. (B) Dispatch above MCL using stored energy.
Operation of Combined Cycles
A power plant must follow different steps to modify its operating load. These processes depend on the start and end points between which the load is varied. This section describes the main cycling processes taken into account for the study and establishes some important assumptions during the operation of the combined cycle (Gonzalez-Salazar et al., 2018).
• Process 1 – start-up: The first process is the start-up of the plant. The turbine, which initially is stopped (“no speed, no load”), increases its speed up to synchronize the generator with the grid frequency (“full speed, no load”). Then, the load raises to the minimum complaint loads that fulfill safety and emission requirements. From this point upwards, the combined cycle may start generating power (Figure 2). The duration of the start-up varies, depending on how long the power plant has been stopped. Standby periods are classified in hot start (0–12 h offline), warm start (12–48 h offline), and cold start (> 48 h offline) (Smith et al., 2020). A standby of 6 h is considered for hot start, 24 h for warm start, and 48 h for cold start. We have also assumed 1-h period to full load for hot start, 2-h period to full load for warm start, and 3-h period to full load for cold start (Smith et al., 2020). Besides that, during start-up, the power output is constrained to the last one-third of the time, at a load equal to the MCL.
• Process 2 – ramping up/down: After start-up, the combined cycle can modify its load to any point between MCL and full load (FL) to satisfy demand. We assume 6% FL/min ramp rate (Gonzalez-Salazar et al., 2018), so passing from MCL to FL takes around 10–15 min. This duration is much shorter than for other processes and therefore neglected in the economic analysis.
• Process 3 – full load: Process 3 represents nominal operation, at which the efficiency of the power plant is the highest and the specific emissions are the lowest.
• Process 4 – minimum load: Process 4 describes the operation at minimum complaint load. This point has the lowest efficiency and the highest specific emissions.
• Process 5 – shutdown: When dispatch is no longer required, the combined cycle has to shut down. The load diminishes at 6% FL/min, so it takes 15–20 min to stop the plant when operating at full load. As simplification, we have also neglected the duration of this process for economic analysis.
• Process 6 – no operation: After shutdown, the combined cycle remains out of operation. There are no incomes throughout this period, so its duration should be minimized. Power to gas will help in avoiding this situation whenever demand is between 30% (MCL) and 20% of full load.
The methodology section covers the scenarios of operation that are analyzed in this study and the techno-economical models used to characterize them. For each hour of the studied period, the load is assumed depending on the scenario described below. With the load, it is possible to calculate the net power production and input energy required. Hourly costs are calculated with this data. When power to gas is running, its power is subtracted from net power and natural gas is stored to be used in the full-load hours. The addition of hourly cost and incomes for the number of operational hours of the period and its comparison with the reference case are used as key variables of the work.
The definition of these scenarios allows the comparison of the conventional operation of combined cycles with the PtG-assisted operation of the hybrid system for situations in which electricity demand falls below the minimum complaint load (< 30% FL, i.e., < 120 MWe). This situation may be due to an increase in RES production or simply a demand reduction. In the first case, it is supposed that there is no RES curtailment. Conventional CCPP have to shut down and follow a “no operation” period in which there are no incomes. On the other side, power-to-gas hybridization avoids shutdown if demand is still above 20% FL. The hybrid CCPP keeps operating at MCL, dispatching the 20% FL demanded by the grid (80 MWe) and diverting the remaining 10% FL (40 MWe) to the power-to-gas system (Figure 3). It has been assumed that the electrolyzers operation is on or off and there is no part-load operation for this equipment. Moreover, the time spent to get back to full-load operation is shorter in the hybrid system since there is no start-up.
Figure 3. Comparison between (A) conventional combined cycle power plant (CCPP) and (B) PtG-assisted CCPP while following an electric demand that falls below the minimum complaint load.
The outage duration under conventional CCPP conditions determines the type of start-up (hot, warm, or cold start). According to that, eight scenarios are defined and grouped to compare the reference case of conventional operation with situations that take advantage of the power-to-gas storage system (Table 1). The time framework within which the analysis is performed (total time of scenario) is fixed in each group to compare equivalent situations. Additionally, scenarios 2, 4, and 7, corresponding to PtG-assisted operation, are analyzed with different loads (30, 50, and 70%). These scenarios are realistic as, although MCL is the typical scenario, it is also usual that the operator asks for increasing loads in the remaining (non-stopped) installations to meet the demand.
A third type of operation is analyzed in scenarios 5 and 8: a temporary peak of demand taking place in the middle of a dispatch that is below the minimum complaint load is considered. Under this situation, the response time of conventional CCPP is very limited since the plant should carry out a warm or cold start-up (Figure 4). Contrarily, the PtG-assisted CCPP is able to satisfy the peak rapidly since the plant keeps working at the virtual MCL. In the quantitative analysis, electricity is diverted to PtG until full-load operation is achieved, as depicted in Figure 4.
Figure 4. Comparison between (A) conventional combined cycle power plant (CCPP) and (B) PtG-assisted CCPP while satisfying a peak of demand that takes place in the middle of a dispatch below the minimum complaint load.
Efficiency Penalty and Emissions
The technical model quantifies the fuel required, the gross/net power produced, and the emissions, by energy and mass balances, in an hourly basis. All these values depend on the load at which the plant operates due to efficiency changes. It should be noted that despite the virtual MCL of the PtG-assisted CCPP being 20%, the actual load at which the plant operates in those situations is 30%.
Different equations to describe the variation in efficiency as a function of partial load can be found in literature (Sjoerd Brouwer et al., 2015). In combined cycles, a decrease of eight to 16 percentage points from full load to MCL is typical (Van den Bergh and Delarue, 2015; de Groot et al., 2017). For this study, we adopt Equation 1, a polynomic curve for the gross efficiency, which is adjusted to a set of different data by de Groot et al. (2017).
Data calculated from Equation (1), for the 400 MWe CCPP of this study, are presented in Table 2. We assume that the specific CO2 emission at full load is 337.7 kg/MWh. As thermal efficiency worsen, these emissions increase to 459.0 kg/MWh for the minimum complaint load (30%).
In the economic model, we calculate the total cost (Equation 2) and incomes (Equation 3) of each type of operation, and then we compared them through the net differential profit. The model is defined in an hourly basis (e.g., hourly OPEX, CAPEX, CO2 taxes, and fuel cost), as for the technical model. Besides that, for the specific situation in which the PtG-assisted CCPP works at the virtual MCL, we consider that the plant operating costs correspond to 30% part load (actual MCL), but the sale of electricity is limited to 20% of the power (virtual MCL).
The CAPEX is assumed as 800 €/kWe for the conventional CCPP (Nalbandian-Sugden, 2016) and 2,600 €/kWe for the power-to-gas plant (Schiebahn et al., 2015; Lee et al., 2019). This value is a conservative figure that includes the sum of the electrolyzer cost, between 500 (Schiebahn et al., 2015) and 1,200–2,000 €/kWe (Lee et al., 2019), and methanation reactor plus compressors (Schiebahn et al., 2015). Moreover, regarding methane storage, the following assumptions can be made. The longest shutdown considered is 48 h, which corresponds to a storage of about 41.5 tons of methane (i.e., 576 MWh). The current commercial tanks for liquefied natural gas (LNG) are in the range of 30–50 tons (The Oxford Institute for Energy Studies, 2018; Linde, 2020), so we could even manage two to three consecutive 48-h shutdowns without emptying the tank. Therefore, the size proposed for our facility keeps within reasonable limits. In terms of cost, liquefaction plants range between 530 and 1,230 €/tpa (tons per annum) (The Oxford Institute for Energy Studies, 2018). As our plant requires a nominal capacity of liquefaction of 0.86 t/h, the corresponding LNG plant would cost 6.8 M€ (assuming 7,500 operating hours and 1,060 €/tpa for a conventional plant, although the liquefaction process in the PtG plant would operate much less hours). Thus, this cost is considered to be already included in the total cost of the PtG plant, which amounts to 104 M€.
Regarding operation costs, fixed OPEX, fuel cost, and shutdowns are considered (Equation 4). Fixed OPEX is set at 25,000 €/MWe/y (ACIL Tasman, 2009). Fuel cost (natural gas) is valued at 25 €/MWhe, according to BP annual report and Netherlands market (BP Statistical Review of World Energy, 2019). Shutdowns are estimated at 14,000, 22,000, and 32,000 € for hot, warm, and cold start-ups, respectively (Kumar et al., 2012). The lifetime of the plant is assumed to be 25 years.
Thus, the specific cost of producing electricity is calculated by adding the OPEX and the CAPEX, distributed throughout 25 years. This electricity production cost ranges from 48.5 €/MWhe (full load) to 72.1 €/MWhe (MCL); for this reason, the electricity price has been set at 65 €/MWh. With lower values, installation is not feasible as the production costs would be higher than the selling price. This value has no important relevance because it also affects the reference case, and in every case, there is a reduction in the electricity production cost. Evidently, electricity price varies considerably throughout the time of day and country, but it is out of the scope of this first analysis to deal with every possibility of price, depending if the power-to-gas installation is in operation or not. We considered to isolate the effect of variable pool prices from the effect of the proposed idea. In Table 3, all the technical and economic data used in the model to calculate these values are gathered.
In this section, each conventional shutdown is compared with the continuous operation at MCL through the utilization of the power-to-gas storage system. The technical and the economic results are gathered in Tables 4–8 for shutdowns of 6-, 12-, and 48-h duration in time frames of 24, 48, and 96 h, respectively.
Scenarios 1 and 2: Hot Start-Up
For the reference case of short shutdown (6 h), a small economic loss is obtained with a specific cost of electricity at 65.44 €/MWh and CO2 emissions at 4% above under full-load conditions. When the PtG system operates and the plant load is kept at minimum complaint load (30%), the profit is not significant and the specific cost of electricity is very similar to that obtained in the reference case. Total and specific emissions of CO2 increase to 13.3 and 5.8%, respectively, due to the higher consumption of fuel and the lower energy efficiency.
If the PtG storage system remains in operation, the trend drastically changes as plant load is raised up to 50 or 70%. Specific CO2 emissions diminish with regards the previous case (scenario 2a), being just 2% above the reference case for scenario 2c (70% FL). An important economic improvement is achieved as the net benefit now becomes positive and increases with load, reaching a marginal profit of roughly 700 and 1,400 €/h, respectively. The specific cost of electricity decreases by more than 2 and 4 €/MWh with respect to the reference scenario, which means a reduction of 3.4 and 6.6%, respectively. In all cases, the cumulative effect of the number of cycles incurred by the turbine and the heat recovery steam generator could be significant in cases of shutdowns and start-ups. This concept would certainly reduce the O&M costs of the combined cycle. From a cautious point of view, calculations do not consider this savings.
The respective marginal profits are above 16,000 and 34,000 €, respectively, per avoided shutdown for a period of 24 h. The significant increase in electricity sale incomes transforms the conventional shutdown situation with economic losses into a profitable operation. It has to be noted that the economic improvement of the alternative modes of operation (continuous MCL via PtG) is not directly related to the stored energy but to the avoidance of shutdown itself.
Scenarios 3 and 4: Warm Start-Up
In reference scenario 3, warm start-up with an outage period of 24 h is analyzed in a time frame of 48 h. Unlike what happened in scenario 1, the losses are now significant, with a negative net profit above 91,000 €. While the CO2 emissions are quite similar, the specific cost of electricity increases up to 75.66 €/MWh, being 16% higher than that for hot start-up.
If the PtG system operates with minimum complain plant load (30%), the net profit is even more negative than in scenario 3, while the specific cost of electricity is slightly lower. The marginal profit with respect to the reference scenario is negative in this case (-119 €/h). Total and specific emissions of CO2 increase to 42.9 and 14.5%, respectively, due to the higher consumption of fuel and a drop in energy efficiency of seven percentage points (pp).
Nevertheless, the outlook changes if the plant load increases (scenarios 4b–4c). Energy efficiency improves to 2 pp for 50% part-load operation and 2 pp more for 70% part-load with regards scenario 4a. Specific emissions decrease but are still 10 and 6% above the reference case, respectively. The economic results are now positive. The specific cost of electricity shows a reduction of 9 and 15%, respectively. In spite of the negative net profit for scenario 4b, marginal profit is positive in both cases: 945 and 2,157 € per hour, respectively, which means total marginal profits of 45,000 and 103,000 € in the reference time framework of 48 h. These figures are 38 and 50% higher than those corresponding to the hot start-up.
As in the previous analysis, the economic improvement under the last two scenarios with continuous operation via PtG is not directly related to synthetic methane production but to the avoidance of shutdown itself.
Scenarios 6 and 7: Cold Start-Up
In reference scenario 6, long outages of 48 h related to cold start-ups are assessed within a total time frame of 96 h. The energy efficiency is similar to scenarios 1 and 3, while specific CO2 emissions are slightly lower due to the different time intervals considered. The specific cost of electricity is 73.83 €/MWh, being 13% higher than that for the hot start-up. As it occurs in scenario 3, the losses are very important, with a negative net profit above 155,000 €.
When the PtG system is included in the analysis with minimum complain plant load (30%), the net profit is even more negative than in scenario 6, while the specific cost of electricity is very similar. The marginal profit with respect to the reference situation is negative for scenario 7a (-318 €/h). Total and specific emissions of CO2 increase to 42 and 14%, respectively, due to the higher consumption of fuel and a drop in energy efficiency of 7 pp.
As presented for warm start-up, the results improve if plant load increases (scenarios 7b–7c). Energy efficiency improves by 2 pp for 50% part-load operation and 2 pp more for 70% part-load with regards scenario 7a. Specific emissions decrease but are still 10 and 6% above the reference case, respectively. The specific cost of electricity shows a reduction greater than 5 and 9 €/MWh at 50 and 70% part load, respectively. The marginal profit is positive in both cases: 705 and 1,870 € per hour, respectively, which means total marginal profits of 67,663 and 179,543 € per long shutdown avoided in the reference time framework of 96 h. For scenarios 7b and 7c, the total marginal profits are four and five times greater than the equivalent of hot start-up, respectively. As in the previous analysis, the economic improvement is mainly caused by the avoidance of shutdown itself.
The study presented in the previous sections has compared the economic and the environmental impact of avoiding hot, warm, and cold shutdowns through the utilization of a power-to-gas energy storage system. From the results, it is deduced that the most influential and uncertain economic parameter to reach profitability is the evolution of electricity demanded to the power plant. This figure depends in principle on the variable renewable generation and the total electricity demand. However, it has to be noted that the required power generation to a particular unit also depends on the availability of the other thermal power plants. Facilities with lower MCL, as those with energy storage systems, have advantage over their competitors and reduce cycling and the number of generation outages. Furthermore, the power initially assigned to those thermal plants which is still available under low demand would be augmented by assuming the power assigned to other thermal plants that have to stop. Therefore, it is highly probable that the former will not have to operate at its MCL for long periods.
Given the principal uncertainties regarding market regulation and power demanded to the PtG-assisted power plant, this section presents a sensitivity analysis to assess the effect of ramping up and down during the analyzed time frameworks. Two additional scenarios are compared to previous cases in Tables 7, 8. Scenarios 5 and 8 show an alternative operation to the conventional warm and cold shutdowns gathered in scenarios 3 and 6. As it was illustrated in Figure 4, there is a transient increase in electricity demand that would hardly be assumed if the unit is off. On the contrary, the CCPP which is still working provides a fast response and can assume the required increase in load.
For scenario 5, the reference time period is still 48 h and full load is required for 12 h during the period in which the conventional power plant (without PtG) undergoes an outage of 24 h. The results are compared with the reference scenario 3 of warm start-up and with scenario 4a where 30% load is fixed. Energy efficiency and specific CO2 emissions reach intermediate values: the former is 4.6 pp above scenario 4a, while the latter is 5% greater than the reference case. The improvement is significant from an economic point of view. The specific cost of electricity decreases almost 11 €/MWh and the marginal profit amounts to 105,000 € with respect to the reference case. Moreover, the net profit turns from negative to positive figures.
A similar trend is observed in Table 8 for the cold start-up situations. Scenario 8 consists in a reference time framework of 96 h and an outage period of 48 h. During this period, the requested power suddenly increases up to 100% load during 24 h. The results are compared with reference scenario 6 of cold start-up and with scenario 7a where load is fixed at MCL. Energy efficiency and specific CO2 emissions reach intermediate values. The efficiency is 4.3 pp above scenario 7a, while specific emissions increase to 5% regarding scenario 6. The improvement is also relevant from an economic point of view. The specific cost of electricity decreases by 10 €/MWh and the marginal profit amounts to 190,500 € with respect to the reference case. The net profit also becomes positive, being 2.5 times the benefit for warm start-up (scenario 5).
Another relevant variable that has to be analyzed in the sensitivity analysis is the power-to-gas size (electrolyzers plus methanation). As a reference case, 10% of the maximum load of the combined cycle was chosen for calculations in order to have enough flexibility to reduce the MCL and get the most of the operational hours in the power-to-gas installation. Table 9 presents the summary of some economic results when the size of the power to gas varies between 10 and 50 MW. It can be concluded that lower sizes of the power-to-gas system led to better economic results in both, avoiding hot and cold shutdowns and start-ups. When the installation size is reduced, it means that more power is available to be sold. As the electricity price is high, the extra incomes surpass the slight increment of total costs. The incremental profit compared with the reference case (40 MW) is not a decisive quantity, around 5% in the case of scenario 7c and up to 20% in scenario 2c due to the low profit results in this case. Here the issue does not depend only on power to gas but also on the incremental flexibility of the combined cycle. For a single avoided stop, the economic results are better with low size of the system, but the flexibility gain is very limited and not enough to avoid the stop. The key variable is the incremental flexibility that determines the operational hours of the system and their feasibility. As it has been explained previously with the electricity prices, the casuistic is huge and specific studies have to be done in a case-by-case basis.
Table 9. Economical comparison by varying the size of the power-to-gas installation for hot (6 h) and cold (48 h): scenarios 2c and 7c.
According to this study, important marginal profits, even net profit, can be achieved if combined cycle power plants utilize power-to-gas technology to avoid shutdowns and extend the capacity factor. The impact of cycling on energy efficiency is damped, but this measure entails a small increase in specific CO2 emissions.
The integration of a combined cycle and a power-to-gas energy storage system is proposed in this study to increase CCPP flexibility of operation and improve economic results under energy systems with high shares of renewable energy sources. This combination allows for a virtual reduction of the minimum complaint load of the CCPP through the diversion of instantaneous excess electricity. The present case study analyses a 400-MWe combined cycle with MCL of 30% that can be virtually reduced to 20% by means of a 40-MWe PtG plant.
Eight scenarios were described to compare the reference case of conventional operation under hot, warm, and cold start-ups with power-to-gas-assisted operation. The results highlight that the hybrid system operating at MCL is not recommended for hot start-ups since the profit obtained is not significant in comparison to that of conventional operation. However, an increase in plant load operation of up to 50–70% dramatically modifies the trend, and a great reduction of specific CO2 emissions is found together with a significant economic improvement. The observed variation is related to the large increase in electricity sale incomes which transforms the conventional shutdown situation with economic losses into a profitable operation.
The economic losses under warm start-up conventional operation are significant and the net profit is strongly negative. The hybrid system of PtG-assisted operation at MCL is still not recommended since its net profits are even more negative. Increments of plant load may again modify this behavior and energy efficiency is improved in higher part-load operation, showing positive economic results. The obtained marginal profits indicate that the hybrid system with CCPP operating with part loads over 50% is profitable and thus recommended.
The behavior of the hybrid system for cold start-up is analogous to the one described for warm start-ups. The economic losses of the reference cold start-up case are very important and the inclusion of the PtG system with the CCPP operating at MCL leads to an even more negative net profit. As presented for warm start-up, the results for higher CCPP loads are much more advantageous with the positive marginal profits. For all the studied cases, the largest amount of economic improvement is related to the avoidance of shutdown.
The analysis of results has pointed out that the most relevant and uncertain economic parameter to reach profitability is the evolution of the amount of electricity demanded to the CCPP. This value is initially related to the variable RES generation and the total electricity demand. It must be highlighted that low electricity demand may remove other thermal power generators with higher MCL of the power pool and leave more room for the participation of our hybrid proposal. Therefore, facilities with lower (real or virtual) MCL present certain advantage over their competitors and reduce cycling and the number of generation outages. To assess these uncertainties related to market regulation and power demanded to the PtG-assisted power plant, several sensitivity analyses have been performed to determine the effect of change load during the time in which the combined cycle should be stopped and the effect of the size of the power-to-gas system. Conclusions in both cases reinforce the finding that the casuistic is huge and specific studies have to be done in a case-by-case basis to achieve detailed and reliable feasibility studies.
According to the results obtained in this study, important marginal profits may be obtained when combined cycle power plants utilize power-to-gas technology to avoid shutdowns and extend the capacity factor. The impact of cycling on energy efficiency is avoided, but this measure entails a small increase in specific CO2 emissions. The use of biogas as source of CO2 for the methanation stage may contribute to balance carbon emissions (Allman et al., 2019; Anghilante et al., 2019). This option should be further investigated in future works because it would also increase the renewable share in the natural gas sector.
Data Availability Statement
All datasets presented in this study are included in the article.
MB, BP, PL, and LR: conceptualization. MB and LR: methodology. MB, BP, and PL: writing. BP and LR: results. BP and PL: validation. MB: artwork. All authors contributed to the article and approved the submitted version.
The work described in this manuscript was supported by the R+D Spanish National Program from Ministerio de Economía y Competitividad, MINECO (Spanish Ministry of Economy and Competitiveness) and the European Regional Development Funds (European Commission), under project ENE2016-76850-R. This work was also supported by the Government of Aragon and co-financed by FEDER 2014-2020 “Construyendo Europa desde Aragón” (Research Group DGA T46_17R and project LMP134_18).
Conflict of Interest
The authors declare that the research was conducted in the absence of any commercial or financial relationships that could be construed as a potential conflict of interest.
We are thankful for the comments and advice given by the reviewers. They have improved the content of this work and pointed out some research directions of particular interest.
CCPP, combined cycle power plants; FFPP, fossil fuel power plants; FSNL, full speed no load; FL, full load; MCL, minimum complaint load; NSNL, no speed no load; O&M, operation and maintenance; PtG, power to gas; REF, reference case; RES, renewable energy sources; VMCL, virtual minimum complaint load.
Allman, A., Palys, M. J., and Daoutidis, P. (2019). Scheduling-informed optimal design of systems with time-varying operation: a wind-powered ammonia case study. Aiche J 65:16434. doi: 10.1002/aic.16434
Andika, R., Nandiyanto, A. B. D., Putra, Z. A., Bilad, M. R., Kim, Y., Yun, C. M., et al. (2018). Co-electrolysis for power-to-methanol applications. Renew. Sustain. Energy Rev. 95, 227–241. doi: 10.1016/j.rser.2018.07.030
Angelidaki, I., Treu, L., Tsapekos, P., Luo, G., Campanaro, S., Wenzel, H., et al. (2018). Biogas upgrading and utilization: current status and perspectives. Biotechnol. Adv. 36, 452–466. doi: 10.1016/j.biotechadv.2018.01.011
Anghilante, R., Müller, C., Schmid, M., Colomar, D., Ortloff, F., Spörl, R., et al. (2019). Innovative power-to-gas plant concepts for upgrading of gasification bio-syngas through steam electrolysis and catalytic methanation. Energy Convers. Manag. 183, 462–473. doi: 10.1016/j.enconman.2018.12.101
Baier, J., Schneider, G., and Heel, A. (2018). A cost estimation for CO2 reduction and reuse by methanation from cement industry sources in Switzerland. Front. Energy Res. 6:5. doi: 10.3389/fenrg.2018.00005
Bailera, M., Hanak, D. P., Lisbona, P., and Romeo, L. M. (2019a). Techno-economic feasibility of power to gas-oxy-fuel boiler hybrid system under uncertainty. Int. J. Hydro. Energy 44, 9505–9516. doi: 10.1016/j.ijhydene.2018.09.131
Bailera, M., Lisbona, P., Llera, E., Peña, B., and Romeo, L. M. (2019b). Renewable energy sources and power-to-gas aided cogeneration for non-residential buildings. Energy 181, 226–238. doi: 10.1016/j.energy.2019.05.144
Bailera, M., Lisbona, P., and Romeo, L. M. (2019c). Avoidance of partial load operation at coal-fired power plants by storing nuclear power through power to gas. Int. J. Hydro. Energy 44, 26063–26075. doi: 10.1016/j.ijhydene.2019.08.033
Bailera, M., Kezibri, N., Romeo, L. M., Espatolero, S., Lisbona, P., and Bouallou, C. (2017a). Future applications of hydrogen production and CO2 utilization for energy storage: hybrid power to gas-oxycombustion power plants. Int. J. Hydro. Energy 42:123. doi: 10.1016/j.ijhydene.2017.02.123
Bailera, M., Lisbona, P., Romeo, L. M., and Espatolero, S. (2017b). Power to gas projects review: lab, pilot and demo plants for storing renewable energy and CO2. Renew. Sustain. Energy Rev. 69, 292–312. doi: 10.1016/j.rser.2016.11.130
Bailera, M., and Lisbona, P. (2018). Energy storage in Spain: forecasting electricity excess and assessment of power-to-gas potential up to 2050. Energy 143, 900–910. doi: 10.1016/j.energy.2017.11.069
Becker, W. L., Penev, M., and Braun, R. J. (2019). Production of synthetic natural gas from carbon dioxide and renewably generated hydrogen: a techno-economic analysis of a power-to-gas strategy. J. Energy Resour. Technol. Trans. ASME 141:021901. doi: 10.1115/1.4041381
BP Statistical Review of World Energy (2019). BP. Full Report - BP Statistical Review of World Energy. Available online at: https://www.bp.com/content/dam/bp/business-sites/en/global/corporate/pdfs/energy-economics/statistical-review/bp-stats-review-2019-full-report.pdf
Brynolf, S., Taljegard, M., Grahn, M., and Hansson, J. (2018). Electrofuels for the transport sector: a review of production costs. Renew. Sustain. Energy Rev. 81, 1887–1905. doi: 10.1016/j.rser.2017.05.288
Buttler, A., and Spliethoff, H. (2018). Current status of water electrolysis for energy storage, grid balancing and sector coupling via power-to-gas and power-to-liquids: a review. Renew. Sustain. Energy Rev. 82, 2440–2454. doi: 10.1016/j.rser.2017.09.003
Capros, P., Vita, A., De Tasios, N., Siskos, P., Kannavou, M., Petropoulos, A., et al. (2016). EU Reference Scenario 2016: Energy, Transport And GHG Emissions. Trends to 2050. Brussels: European Union.
Chauvy, R., Dubois, L., Lybaert, P., Thomas, D., and De Weireld, G. (2020). Production of synthetic natural gas from industrial carbon dioxide. Appl. Energy 260:114249. doi: 10.1016/j.apenergy.2019.114249
Chen, S., Wei, Z., Sun, G., Wang, D., Zhang, Y., and Ma, Z. (2018). Stochastic look-ahead dispatch for coupled electricity and natural-gas networks. Electr. Power Syst. Res. 164, 159–166. doi: 10.1016/j.epsr.2018.07.038
Colbertaldo, P., Agustin, S. B., Campanari, S., and Brouwer, J. (2019). Impact of hydrogen energy storage on California electric power system: towards 100% renewable electricity. Int. J. Hydro. Energy 44, 9558–9576. doi: 10.1016/j.ijhydene.2018.11.062
Cormos, A. M., Dinca, C., Petrescu, L., Andreea Chisalita, D., Szima, S., and Cormos, C. C. (2018). Carbon capture and utilisation technologies applied to energy conversion systems and other energy-intensive industrial applications. Fuel 211, 883–890. doi: 10.1016/j.fuel.2017.09.104
de Groot, M., Crijns-Graus, W., and Harmsen, R. (2017). The effects of variable renewable electricity on energy efficiency and full load hours of fossil-fired power plants in the European Union. Energy 138, 575–589. doi: 10.1016/J.ENERGY.2017.07.085
Di Salvo, M., and Wei, M. (2019). Synthesis of natural gas from thermochemical and power-to-gas pathways for industrial sector decarbonization in California. Energy 182, 1250–1264. doi: 10.1016/j.energy.2019.04.212
European Commission (2018). Directive (EU) 2018/2001 Of The European Parliament And Of The Council Of 11 December 2018 On The Promotion Of The Use Of Energy From Renewable Sources. Brussels: European Commission.
Gahleitner, G. (2013). Hydrogen from renewable electricity: an international review of power-to-gas pilot plants for stationary applications. Int. J. Hydro. Energy 38, 2039–2061. doi: 10.1016/j.ijhydene.2012.12.010
Giglio, E., Lanzini, A., Santarelli, M., and Leone, P. (2015). Synthetic natural gas via integrated high-temperature electrolysis and methanation: part I-energy performance. J. Energy Storage 1, 22–37. doi: 10.1016/j.est.2015.04.002
Gonzalez-Salazar, M. A., Kirsten, T., and Prchlik, L. (2018). Review of the operational flexibility and emissions of gas- and coal-fired power plants in a future with growing renewables. Renew. Sustain. Energy Rev. 82, 1497–1513. doi: 10.1016/J.RSER.2017.05.278
He, G. X., Yan, H., Chen, L., and Tao, W. Q. (2020). Economic dispatch analysis of regional electricity-gas system integrated with distributed gas injection. Energy 201:117512. doi: 10.1016/j.energy.2020.117512
He, L., Lu, Z., Zhang, J., Geng, L., Zhao, H., and Li, X. (2018). Low-carbon economic dispatch for electricity and natural gas systems considering carbon capture systems and power-to-gas. Appl. Energy 224, 357–370. doi: 10.1016/j.apenergy.2018.04.119
Jensen, S. H., Graves, C., Mogensen, M., Wendel, C., Braun, R., Hughes, G., et al. (2015). Large-scale electricity storage utilizing reversible solid oxide cells combined with underground storage of CO2 and CH4. Energy Environ. Sci. 8, 2471–2479. doi: 10.1039/c5ee01485a
Kumar, N., Besuner, P., Lefton, S., Agan, D., and Hilleman, D. (2012). Power Plant Cycling Costs. National Renewable Energy Laboratory. Available online at: https://www.nrel.gov/docs/fy12osti/55433.pdf
Lee, B., Lee, H., Heo, J., Moon, C., Moon, S., and Lim, H. (2019). Stochastic techno-economic analysis of H2 production from power-to-gas using a high-pressure PEM water electrolyzer for a small-scale H2 fueling station. Sustain Energy Fuels 3, 2521–2529. doi: 10.1039/c9se00275h
Lew, D., Brinkman, G., Kumar, N., Lefton, S., Jordan, G., and Venkataraman, S. (2013). “Finding flexibility. cycling the conventional Fleet,” in Proceedings of the IEEE Power Energy Magazine, Piscataway, NJ.
Lisbona, P., Frate, G. F., Bailera, M., and Desideri, U. (2018). Power-to-gas: analysis of potential decarbonization of spanish electrical system in long-term prospective. Energy 159, 656–668. doi: 10.1016/J.ENERGY.2018.06.115
Matute, G., Yusta, J. M., and Correas, L. C. (2019). Techno-economic modelling of water electrolysers in the range of several MW to provide grid services while generating hydrogen for different applications: a case study in Spain applied to mobility with FCEVs. Int. J. Hydro. Energy 44, 17431–17442. doi: 10.1016/j.ijhydene.2019.05.092
Naval, N., Sánchez, R., and Yusta, J. M. (2020). A virtual power plant optimal dispatch model with large and small-scale distributed renewable generation. Renew. Energy 151, 57–69. doi: 10.1016/j.renene.2019.10.144
Pierre, I., Bauer, F., Blasko, R., Dahlback, N., Dumpelmann, M., Kainurinne, K., et al. (2011). Flexible Generation: Backing Up Renewables. Available online at: https://www.google.com/url?sa=t&rct=j&q=&esrc=s&source=web&cd=&ved=2ahUKEwjv-IKvu7vqAhWJohQKHYWICFkQFjAAegQIAxAB&url=https%3A%2F%2Fwww3.eurelectric.org%2FDownload%2FDownload.aspx%3FDocumentFileID%3D71337&usg=AOvVaw3Idw040czr6Pa6RLx3uqsy
Romeo, L. M., Peña, B., Bailera, M., and Lisbona, P. (2018). “Analysis of the influence of Power-to-Gas systems in cyclic performance of fossil fuel power plants. ECOS 2018,” in Proceedingsof the 31st International Conference on Efficiency, Cost, Optimization, Simulation and Environmental Impact of Energy Systems, Braga.
Rosenfeld, D. C., Böhm, H., Lindorfer, J., and Lehner, M. (2020). Scenario analysis of implementing a power-to-gas and biomass gasification system in an integrated steel plant: a techno-economic and environmental study. Renew. Energy 147, 1511–1524. doi: 10.1016/j.renene.2019.09.053
Schemme, S., Samsun, R. C., Peters, R., and Stolten, D. (2017). Power-to-fuel as a key to sustainable transport systems - an analysis of diesel fuels produced from CO2 and renewable electricity. Fuel 205, 198–221. doi: 10.1016/j.fuel.2017.05.061
Schiebahn, S., Grube, T., Robinius, M., Tietze, V., Kumar, B., and Stolten, D. (2015). Power to gas: technological overview, systems analysis and economic assessment for a case study in Germany. Int. J. Hydro. Energy 40, 4285–4294. doi: 10.1016/j.ijhydene.2015.01.123
Sjoerd Brouwer, A., Van Den Broek, M., Seebregts, A., and Faaij, A. (2015). Operational flexibility and economics of power plants in future low-carbon power systems. Appl. Energy 156, 107–128. doi: 10.1016/j.apenergy.2015.06.065
Smith, R. W., Polukort, P., Maslak, C. E., Jones, C. M., and Gardiner, B. D. (2020). GE Power Systems Advanced Technology Combined Cycles. Report from General Electric 592. Atlanta, GA: GE Power Systems.
Vandewalle, J., Bruninx, K., and D’haeseleer, W. (2015). Effects of large-scale power to gas conversion on the power, gas and carbon sectors and their interactions. Energy Convers. Manag. 94, 28–39. doi: 10.1016/j.enconman.2015.01.038
Wang, X., Bie, Z., Liu, F., and Kou, Y. (2019). Robust dispatch for integrated electricity and natural gas system considering wind power uncertainty. Energy Proc. 159, 130–135. doi: 10.1016/j.egypro.2018.12.030
Keywords: flexibility, energy storage, power to gas, combined cycle, synthetic methane, CO2 utilization
Citation: Bailera M, Peña B, Lisbona P and Romeo LM (2020) Improved Flexibility and Economics of Combined Cycles by Power to Gas. Front. Energy Res. 8:151. doi: 10.3389/fenrg.2020.00151
Received: 31 March 2020; Accepted: 16 June 2020;
Published: 14 July 2020.
Edited by:Tao Wang, Zhejiang University, China
Reviewed by:Menglian Zheng, Zhejiang University, China
Robert J. Braun, Colorado School of Mines, United States
Copyright © 2020 Bailera, Peña, Lisbona and Romeo. This is an open-access article distributed under the terms of the Creative Commons Attribution License (CC BY). The use, distribution or reproduction in other forums is permitted, provided the original author(s) and the copyright owner(s) are credited and that the original publication in this journal is cited, in accordance with accepted academic practice. No use, distribution or reproduction is permitted which does not comply with these terms.
*Correspondence: Manuel Bailera, email@example.com